They are suitable for indoors telecommunication fixed installation.
DIN VDE 0815
Conductors consist of solid copper having a diameter of 0.6 mm and 0.8 mm.
Conductors are insulated with PVC according to VDE 0207.
This product is no longer in stock
Warning: Last items in stock!
Pairs are stranded together in concentic layers .
The color identification of the wires is in compliance with the VDE 0815.
A polyester tape is applied over the cable core
Over the wrapped core is applied a plastic coated aluminum foil.
The Drain wire consists of red copper that has a diameter of 0.4 mm for cables having a maximum capacity of 10 pairs and 0.6 mm diameter for cables with more than 10 pairs.
1- Capacitance (800 Hz) -> Max.100 nF/km
2- Insulation resistance -> Min.100M? .km
3- Electrical resistance
---0,6 mm conductors -> Max.130? /km
---0,8 mm conductors -> Max.73,2? /km
4- Capacity unbalance at (800 Hz) -> Max.300pF/100ml
5- Test voltage 800 V DC
6- Operating voltage 300V
Coils : 100m; 250m
Drums : 500 or 1000m